REF630 PLC is designed and produced by company ABB. This PLC exchanged older series PLC’s REF541/543/545. REF630 PLC is used mainly for protection of incoming cubicles, sectional cubicles, voltage transformers, feeders, capacitor banks and so on. This PLC is also used in automatic schemes: automatic transfer scheme (ATS), under frequency load shedding (UFLS) and so on.
Technical manual of PLC REF630 you can find in document RE_630_technical manual.
In maintenance it is convenient to use on-line mode of PLC REF630. In on-line mode you can explore status of binary inputs, binary outputs, also status of internal signals and interlockings. It is very usefull function at searching failures in schemes. PLC REF630 is configuring by using software PCM600. FBD programming language is used to configuring PLC REF630. How download, install and set PCM600 software read article “PCM600 ver2.8 engineering programming tool installation“.
PLC REF630 has also disturbance recorder and event list.
In this article we are going to read existing configuration, event list, records of distrubance recorder from PLC REF630 by using PCM600 ver.2.8 sowftware in Windows 10 operating system.
Sequence of article:
- Reading communication settings of PLC REF630.
- Setting communication settings of Windows 10 operating system.
- Connecting PLC REF630 to PC and testing connection between them.
- Creating project in PCM600 for PLC REF630.
- Verifying technical key.
- Reading existing configuration and settings from PLC REF630.
- Reading event list from PLC REF630.
- Reading and saving records of distrubance recorder from PLC REF630.
- Reading communication settings of PLC REF630.
REF630 PLC is configuring by using PC. Therefore you need to connect PLC to PC by using communication cable. The connection between PLC and PC will successfully be established when we set correct communication settings of Windows 10 operating system: these settings are „IP address“ and „Subnet mask“. These settings of PLC REF630 are set by manufacturer ABB and are not editable. So we need first to read communication settings of PLC REF630 on HMI by manual operation and then to set these communication settings to Windows 10 operating system.
Window „Main menu“ appears:
Select „Configuration“ by using button „to down“:
Press button „to the right“ to enter in „Configuration“. Select „Communication“ on window „Main menu/Configuration“ by usig button „to down“:
Press button „to the right“ to enter in „Communication“. Select option „TCP-IP configuration“:
Press button „to the right“ to enter in „TCP-IP configuration“. Select option „Front port“:
Press button „to the right“ to enter in „Front port“. On window „…/TCP-IP configuration /Front port“ you can see required communication parameters:
Front port address of PLC REF630 is 192.168.0.254, therefore we are going to use IP address, fo example 192.168.0.253 in PC. These IP addresses must be differrent. „IP mask“ = 255.255.255.0, the same IP mask we’re going to enter for Windows 10 (parameter “Subnet mask”).
to return to main HMI menu.
2. Setting communication settings of Windows 10 operating system.
Select „Network“ icon on desktop and by pressing on right mouse button select „Properties“:
Press „Change adapter settings“:
Select „Ethernet“ and by pressing on right mouse button select „Properties“:
On window „Ethernet Properties“ select „Internet Protocol Version 4 (TCP/Ipv4)“ and press button „Properties“:
Window „Internet Protocol Version 4 (TCP/Ipv4) Properties“ appears. Here you schould enter required parameters „IP address“ and „Subnet mask“:
Enter „IP address“ ir „Subnet mask“ as shown in the figure 17:
Press button „OK“.
Close window „Ethernet Properties“ by pressing button „Close“:
Ethernet communication settings of Windows 10 operating system are set.
3. Connecting PLC REF630 to PC and testing connection between them.
We‘re going to connect PLC REF630 to PC by using ethernet communication cable:
Connect one communication cable lead to front port of REF630 PLC as shown in the figure:
Other communication cable lead connect to PC‘s ethernet port:
Now we need to test connection between PC and PLC REF630.
Select „Start-Command Prompt“:
Window „Command Prompt“ appears:
Enter command „ping“ and IP adress of PLC REF630 „192.168.0.254“. Press button „Enter“:
Connection between PLC REF630 and PC is succesfully established. Received data prove us this fact:
Ping statistics for 192.168.0.254:
Packets: Sent = 4, Received = 4, Lost = 0 (0% loss)
We sent four data packets from PC to PLC REF630 and received all data packets back to PC from PLC REF630. Lost data is 0%.
Next step – creating project of PLC REF630 in PCM600 application.
4. Creating project in PCM600 for PLC REF630.
Run application PCM600:
Select „File- Open/Manage Project…“:
Press button „New Project“:
Enter project name. For example „SUB1-REF630“ and press button „Create“:
On window „Open/Manage Project“ select „SUB-1_REF630 project and press button „Open Project“:
Select SUB-1_REF630 and by pressing on right mouse button sellect „New-General-Substation“:
Select „Substation“ and by pressing on right mouse button sellect „New-General-Voltage Level“:
Select „Voltage Level“ and by pressing on right mouse button sellect „New-General-Bay“:
Select „Bay“ and by pressing on right mouse button sellect „New-Feeder IEDs-REF630“:
On window „REF630 – Configuration Mode Selection Page“ we schould decide in which mode we‘re going to work. Pick „Online configuration“ mode, because you don‘t have configuration file of PLC REF630 yet. We are going to read this file from PLC REF630.
Select „Online configuration“ and press „Next“:
On window „REF630 – IEC61850 communication protocol“ select „Front port“. This port will be used because we have connected communication cable to them (see figure 21). Enter IP address of PLC REF630 192.168.0.254 (this IP is defined by manufacturer to PLC REF630, see figure 8).
On window „REF630 – Version Selection Page“ press button „Scan“ to read IED type and product version of PLC REF630:
In my case PLC version is 1.2.0. Press button „Next“:
Press button „Scan“ to read order code of REF630. order code show us various charachteristic of REF630: types of protections, communication protocols, number of binary inputs and outputs.
In the figure 41 it is clear that PLC REF630 is used to protect feeder (Main application = F, Feeder protection and control).
Press button „Next“.
On window „REF630 – Setup Complete Page“ press button „Finish“.
Project of PLC REF630 is created. Now we need to read existing internal configuration and settings from IED REF630.
The configuration is empty at this moment (see option „Application Configuration“ in project‘s tree):
5. Verifying technical key.
After creating project we need to check versions of projects of PCM600 application and PLC REF630. Technical keys show us either these versions are the same or differ. These technical keys must be same otherwise we coudn‘t read configuration from REF630. if technical keys differ you must enter your new defined tehnical key (enter this key in folder „User-defined Technical Key“) and press button „OK“. This new technical key will be given to PCM600 and PLC REF630.
In project‘s tree select REF630 and by pressing right mouse button select „Set Technical Key“:
Press button “OK”:
Reading technical key from REF630:
On window bellow we see that techical keys of PCM600 and PLC‘s REF630 are identical (AA1JQ01B101):
We don‘t need to set new technical key so press button „Cancel“ to exit.
6. Reading existing configuration and settings from PLC REF630.
First you schould read existing configuration from REF630 and then read settings of protections. Mark „REF630“ on project tree and by pressing right mouse button select „Read from IED“:
Press button „Yes“ to start reading the configuration from PLC REF630:
Reading configuration from PLC REF630:
The configuration of REF630 readed successfully:
To open downloaded configuration, select „Application Configuration“ on project‘s tree and by pressing right mouse button select „Application Configuration“:
On right side you can explore application configuration window:
Application configuration consists of 11 sheets: „BI_DR“, „BO_TRP“, „BAY“, „FIXED“, „QA“, „U_PROT“, „I_PROT“, „OTHER“, „MEASURING“, „LED“, „IEC103“.
Configuration of REF630 is downloaded. Now we are going to read settings of funcion block PHIPTOC (overcurrent protection instantenous stage, see RE_630_technical manual). Select „Application Configuration“ on project‘s tree and by pressing on right mouse button select „Parameter Setting“:
On „Application Configuration“ window select sheet „I_PROT“ and in opened worksheet select function block „PHIPTOC“:
Select on right side „REF630 16 31 – Parameter Settings“. Here you can explore settings of function block „PHIPTOC“:
Overcurrent instant stage starts at 12xpu=12x5A=60A and tripping time of this protection is 0,05 sec.
In this way you can read any settings of protections. The configuration and settings of PLC REF630 are successfully readed.
Save file by selecting „File-Save“.
7. Reading event list from PLC REF630.
Select „REF630 16 31“ on project‘s tree and by pressing right mouse button select „Event viewer“:
Window of event list appears (window „REF630 16 31 – Event viewer“):
Save downloaded event list by selecting „File-Save“. After downloading and saving of event list, later you can explore this event list in PCM600 application. You don‘t need each time to connect to PLC REF630 to explore this event list of PLC REF630. After occuring new events, you can download these new events by connecting to PLC REF630.
8. Reading and saving records of disturbance recorder from PLC REF630.
Select „REF630 16 31“ on project‘s tree and by pressing on right mouse button select „Disturbance Handling“:
On right side window „REF630 16 31 – Disturbance Handling“ by pressing right mouse button select „Read Recordings Information“:
List of records of disturbance recorder appears:
On record 2017-09-02 13:06:05.079 press twice on left mouse button. Computer icon on record 2017-09-02 13:06:05.079 transfomed from grey color to blue color:
Select record 2017-09-02 13:06:05.079 and by pressing on right mouse button select „Create Report“:
Disturbance report will be created in pdf format:
You can explore disturbance by using this disturbance report file.
Save this report by selecting „File-Save“.
We‘ve learned how to create project of REF630, how to download configuration file, event lis, disturbance record of PLC REF630.
Close PCM600 application by selecting „File-Exit“: